Total Harmonic Distortion (THD) Power Factor Measurements for Voltage and Current Distortions
Key Takeaways

Total harmonic distortion (THD) is the measure of the deviation of voltage or current waveform from ideal sinusoidal shape.

True Power Factor= Distortion Factor x Displacement Factor

Electrical equipment manufacturers follow the recommended harmonic standards to limit the harmonic emission from their products and ensure the protection of the equipment from the supply voltage or current harmonics.
The nonsinusoidal periodic voltage can be decomposed into sinusoidal voltages of fundamental frequency and frequencies that are integer multiples of the fundamental frequency.
Right now, if you’re reading from a laptop, check the input details given in your AC adapter. Typically, you’ll find a voltage range in an interval of 100240 V, with a frequency between 5060 Hz. This input spec includes the globally recognized singlephase, pure sinusoidal, utility voltage standards of either 120 V, 60 Hz, or 240 V, 50 Hz. However, as an electrical enthusiast, you are probably aware of the realtime deviation of supply voltage from the abovementioned shape, amplitude, and frequency standards.
The occurrence of these distortions is generally considered under the umbrella term ‘Power Quality’ issues. As the density of nonlinear devices on a per capita basis drastically increases worldwide, Power Quality (PQ) is becoming a matter of great concern.
The proliferation of nonlinear loads introduces sinusoidal voltage components with small frequencies into the power system. These voltage components—called voltage harmonics— superimpose with the fundamental frequency voltage and make the utility supply voltage nonsinusoidal. The nonsinusoidal voltage supply results in heating losses in machines, malfunctioning of sensitive equipment, and communication interferences. Total harmonic distortion (THD) is the measure of the deviation of voltage or current waveform from ideal sinusoidal shape. THD quantifies the unwanted harmonics that are present in the voltage or current waveforms using Fourier analysis. THD analysis is crucial for maintaining and enhancing power system stability.
Decoding THD
If you are listing the common harmonic sources in a power system, you can't miss the power electronic converters, adjustable speed drives, static VAR compensators, and SMPS. These sources generate either current or voltage harmonics, which are mutually inclusive in nature. Given a chance to filter out the fundamental frequency voltage component v1(t) from a nonsinusoidal voltage v(t), what remains is the entire harmonics given by vh(t):
The input voltage specification printed in any equipment is the RMS voltage of the fundamental frequency (f) component, V1. The harmonics vh(t) gatecrashes to transform the ideal voltages or currents to an undesirable shape, amplitude, and frequency. The harmonics vh(t) can be decomposed into several sinusoidal components at frequencies which are integer multiples of the fundamental frequency, f. If v(t) constitutes a sinusoidal voltage component with a frequency equal to n times f, it forms the nth harmonics vn(t). The nth harmonic vn(t)supplies its share to the amplitude of the nonsinusoidal voltage v(t). The value of n could be 2, 3, or 4, and so on, but even harmonics rarely exist.
THD can be mathematically expressed in percentages with the following equation, where Vnis the RMS voltage of nth harmonic, and V1is the RMS voltage of the fundamental frequency component:
The same THD equation is applicable to current harmonics as well.
Upshots of Harmonics
From the discussion so far, it is clear that harmonics are like uninvited guests. The presence of harmonics can be catastrophic to power system components such as electrical machines, electronic devices, measuring instruments, switchgear, transmission cables, and lighting systems.
Electrical Machines
An integral part of the power system is occupied by electrical machines such as motors, generators, and transformers. When saturated, the ferromagnets in these machines act as the epicenter of the harmonics. We are familiar with the hysteresis and eddy current losses in machines, which are frequency dependent. The presence of higherorder harmonics in the input supply aggravates the magnetic losses in motors and transformers, hence the temperature.
Coming to the rotor side of motors, the distortions in rotor currents cause torque pulsations or reduced torque. The current distortion also causes increased copper losses and heating in the electrical machines, thus probing a serious threat to insulation. It's right to cite the cogging and crawling phenomena in induction motors as an example in this context.
Apart from voltage, generators are also suppliers of 3rd harmonics or triplen harmonics into the power system. The current and voltage harmonics propagate from the generator to other loads present in the bus, polluting the system.
No one is fond of the humming noises from machines—supplying an electrical machine with a distorted supply voltage is like turning the humming volume to high.
Electronic Devices
Have you ever taken a malfunctioning electronic gadget to a service center, only to find it works perfectly fine once you are at the store? The service center personnel usually blame the input power the device was plugged into. It's true that most electronic devices maloperate under distorted input voltage. The harmonics in the input voltage shift the zerocrossing points in the waveform, influencing the performance of internal clocks, timers, and ADCs.
Power electronic converters and switching circuits are the main sources distorting the shape of currents and voltages in a power grid. They are also the victims; the commutation of the firing devices are mostly jeopardized by the harmonics in the source voltage. The functioning of resonant converters and linecommutated converters is challenged by the harmonics, and the consequences are frequent in microgrid systems.
The Information Technology Industry Council (ITIC) has studied the vulnerability of computers to the distorted power supply. These studies have resulted in set standards limiting harmonic effects. The hangs, loss of data, or glitches in process control due to harmonics can't be neglected when it comes to industrial automation. Additionally, in communication electronics, we might experience crosstalks and interferences in the presence of harmonics in neighboring transmission lines. Communication engineers are very keen on attending to this problem and resolving interference and noise disturbances.
Redefining the Term ‘Power Factor’
We usually define the power factor as the cosine of the angle between the voltage and current. As voltages and currents composed of harmonics are nonsinusoidal in nature, we will see how to define the power factor:
Assuming a power system with harmonic free voltage vin (t) and distorted current iin (t):
where Vin is the RMS value of system voltage, and Iin1is the RMS value of the fundamental component of the distorted current. 1is the angle between the vin and iin1 . The higherorder current harmonics do not contribute to the average power drawn from the system.
Substituting equations (4) and (5) into equation(3), PF reduces to
where Iin1Iinis the distortion factor (DF), and cos1is the displacement factor (DPF). Using equation (1) in the context of current harmonics, equation (6) can be rewritten as
Ensuring Harmonic Compatibility in Nonlinear Devices
The harmonic control in electric power systems and equipment is guided by various standards such as IEEE Standard 5192014, IEC 6100036, and NEMA IS07 P12019, among others. THD analysis offers a breakthrough in determining the harmonics present in the current or voltage under consideration. THD analysis conducted in a suitable simulation platform safeguards the reliability of your design by informing the percentage of harmonics superimposed in the waveforms.
When dealing with power systems, it is important to keep an eye on both voltage and current harmonics. Both of these distortions have drawbacks: less efficiency, an increase in current, insulation problems, incorrect relay trippings, and switchgear failures. Nonlinear loads are the main problem makers, and there is a need for matchmaking between the design of these non linear devices and THD standards.